7 of 7Image
Here is where power is supplied to the racks. Each fully-loaded module can draw down a maximum power load of 232kW.
The facility is currently being certified by the Uptime Institute as a Tier 3 facility. This requires the facility to have multiple redundant capacity components and multiple distribution paths serving the computer equipment, hence the two separate power cables.